LGS bed elevator provides optimal riding space and safety door system to transport patient bed as well as comfortable ride for the safety of patients. Furthermore, It was adopted permanent magnetic gearless tractionmachine and variable voltage variable frequency control system providing significant energy saving.
Adopt permanent magnetic gearless traction machine and VVVF Control module, so that the elevator is more quite and smooth trip. Fresh atmosphere in car, release patient stress, it offers protection from unwanted jolts giving a ride of comfort
Excellent door safety features (infrared beam sensor) for stretcher and passenger is provided And wide entrance opening width and qukck response telescopic door system is adopted for hospital bed transport.
BED ELEVATOR CAR DESIGN BED Modern-HL 01
BED ELEVATOR CAR DESIGN BED Modern-HL 02
BED ELEVATOR CAR DESIGN BED Deluxe-MR 01
BED ELEVATOR CAR DESIGN BED Luxury-Art Film 01
PLANNING GUIDE Hospital BED - Gearless
|BED (Hospital) Elevator (Non Code Area)||[unit : mm]|
|11||800||1100||1300||2300||2150||2900||4450||2900||7900||6100||5.0 / 8.0 / 9.0||2400||4400 / 4500 / 4600||1400 / 1600|
|15||1000||1100||1500||2300||2350||2900||4850||2900||11600||8500||6.3 / 10.0 / 11.7||2400||4400 / 4500 / 4600||1400 / 1600|
|17||1150||1200||1500||2500||2520||3000||5190||3000||11800||8700||7.7 / 11.5 / 13.5||2400||4400 / 4500 / 4600||1400 / 1600|
|11||800||1100||1300||2300||2150||2900||4450||2900||8400||6600||10.0 / 15.0||2500||5000 / 5500||2100 / 2400|
|15||1000||1100||1500||2300||2350||2900||4850||2900||12100||9000||13.4 / 16.7
||2500||5000 / 5500||2100 / 2400|
|17||1150||1200||1500||2500||2520||3000||5190||3000||12300||9200||15.4 / 19.2||2500||5000 / 5500||2100 / 2400|
BED (Hospital) Elevator (Non Code Area)
|BED (Hospital) Elevator (Code Area:EN-81)||[unit : mm]|
|20||1350||1100||1300||2300||2150||2900||4450||2900||9100||6200||9.0 / 13.5 / 15.8||2400||4400 / 4500 / 4600||1400 / 1600|
|24||1600||1200||1500||2300||2350||2900||4850||2900||11900||8800||10.7 / 16.0 / 18.7||2400||4400 / 4500 / 4600||1400 / 1600|
|28||2000||1200||1500||2500||2520||3000||5190||3000||12100||9000||13.4 / 20.0 / 23.4||2400||4400 / 4500 / 4600||1500 / 1700|
|20||1350||1100||1300||2300||2150||2900||4450||2900||9600||6700||18.0 / 22.5||2500||5000 / 5500||2100 / 2400|
|27||1600||1200||1500||2300||2350||2900||4850||2900||12400||9300||21.4 / 26.7||2500||5000 / 5500||2100 / 2400|
|28||2000||1200||1500||2500||2520||3000||5190||3000||12600||9500||26.7 / 33.4||2500||5000 / 5500||2100 / 2400|
BED (Hospital) Elevator (Code Area:EN-81)
|Full collective selective||In automatic running or attendant state,
this function enables the elevator to respond both car calls and hall
Passengers at any service floor can call the elevator by pressing the up call button and down call button.
|Anti-nuisance function||The system automatically judges the number
of passengers in the car and compares it with the number of registered
If there are excessive car calls, the system determines that it is nuisance and cancels all car calls. In this case, passengers need to register correct car calls again.
|Car Call Cancellation||Passengers can press the button consecutively twice to cancel wrong calls.||●|
|Turn Off of Car Light
|If there is no running command within the set time, the system automatically cuts off the power supply to the lamp and fan in the car.||●|
|Full-load direct runnung||When the car is full-loaded in automatic
running state, the elevator does not respond to hall calls from the
passing floors. These halls calls, however,
can still be registered, and will be executed at next time of running (in the case of single elevator) or by another elevator
(in the case of parallel/group control).
|Overload protection||When the car load exceeds the rated elevator load, the elevator alarms and stops running.||●|
|Button stuck check||The system can automatically identify
whether a hall call button is stuck and cancel the stuck call,
preventing the condition that the elevator cannot close and run due to stuck hall calls.
|Repeat door close||If the door lock is not applied after
the elevator performs door close for a certain time, the elevator
automatically opens the door and then closes the
|Automatic door open upon door
|If the system detects that the door lock
circuit is abnormal during door open/close, the elevator automatically
opens and closes the door again,
and reports a fault after the set door open/close times is reached.
|Door open time setting||The system automatically determines different
door open time for door open for call, command, protection,
or delay according to the set door open holding time.
|Arrival gong disabled at night||Within the set time period, the arrival gong is disabled.||●|
|Landing at another floor||If the door open time exceeds the door open protection time but the door open limit signal is still inactive, the elevator closes the door and then automatically runs to the next landing floor.||●|
|Voice Announcement||The elevator automatically announces information
such as the running direction and next arriving floor
|Forced door close||When the door fails to close within the
set time due to the action of the light curtain or safety edge, the
elevator enters the forced door close state,
closes the door slowly, and gives a prompt tone.
|Group control||The system supports parallel control of two elevators / group control of more than three elevators||○|
|Micro Leveling||After landing at a floor, the elevator
may move upward or downward due to the load change and the car door
is not aligned with the ground,
which is inconvenient for in and out of passengers and goods. In this case, the system allows the elevator to run to the leveling position in the door
open state at the leveling speed.
|Light curtain signal judgment||If the door is blocked by stuff during door close, the light curtain acts and the elevator opens the door. This function is invalid in fire emergency state.||○|
|Power failure emergency
|For the elevator configured with standby
power supply, the system uses the standby power supply (ARD System)
to implement low-speed self-rescue
in the case of power failure.
|Residential monitoring||The control system can be connected to
the terminal in the monitoring room. By using the NEMS software,
you can view the floor position, running direction, and fault state of the elevator.
|Parking Operation||In order for park the elevator, if the
parking key is on position the car stop at the specified floor after
finish servicing of all of registered call.
After the car stops at the specified floor, the car light and fan are off automatically and every buttons both on the car operating panel and
hall button box are no more available.
|Fire return Operation||In case of fire every cars should be returned to the specified floor in order to evacuate passengers safety.||○|
|Fireman Operation||In case of fire, a fireman can use the elevator which is stopped at the specified floor in order to support fireman for fire-fighting.||○|
The works below are not included in the elevator installation work and should be carried out by building contractors in accordance with our drawing, relevant international or codes and regulations.
-A property framed and enclosed hoistway, including any ventilation as required by the governing code or authority.
-A dry pit constructed to the elevator manufacture's specifications to reinforce or sustain any vertical forces on the guide rails impacted loads from the car and counterweight buffers.
-A metal still angle or concrete haunch across the full width of the hoistway at each elevator landing.
-Provision of steel bars to fix jamb around the entrance of each floor.
-All cutting, including cutouts to accommodate hall signal fixtures, patching, painting of wall, floors, or partitions, together with finish painting of entrance doors and frame, if required.
-Provision of entrance or ladder for pit access.
-Supply and installation of fascia plate
-Installation of emergency exits and electric wiring in blind sections of hoistway where required.
-the tolerance of emergency exits and electric wiring in build sections of hoistway where required.
-The tolerance of perpendicular line over the whole hoistway height must not exceed ±30mm.
-A waterproof outlet and light fixture in the elevator pit area with the light switch being located adjacent to the access door ladder.
-Suitable light fixture and convenience outlet in the pit with a light switch adjacent to the access door or ladder. The receptacles shall have protection for ground.
-Provision of wiring between controller and building management system.
-A construction hoisting beam or hook, if require, with the correct location and size as determined by elevator contractor for each hoistway.
-Noise insulation should be installed between machine room and adjacent residential area.
-A suitable machine room with legal access, ventilation and concrete floor . The temperature in the machine room should be maintained between 5℃ and 40℃ Relative humidity should not exceed 90%(monthly) and 95%(daily) non-condensing.
Ventilation fan or air conditioner should be provided as per heat dissipation by the elevator contractor.
-The size of entrance shall be min. 1000mm(w) X 2000mm(H).
-Installation of lead-in wire and earth wire between building main power board and room incoming distribution board. However, machine room lighting source supply shall be install separately.
-Provision of suitable light fixture and convenience outlets in the machine room.
-Wiring and piping between each machine room and monitoring system.
-Machine room and hoistway shall be free or harmful gas.
-All electric power for lighting, tools, welding, etc during installation.
-All single phase receptacles installed in machine room, pit and machinery spaces shall ground fault circuit interrupter
-Fire detector for emergency operation.
- A secured area for storage of elevator equipment and materials during installation.